---
product_id: 185057418
title: "Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1"
brand: "siemens"
price: "$2254047"
currency: COP
in_stock: true
url: https://www.desertcart.co/products/185057418-air-velocity-sensor-range-0-to-5-10-15-m
store_origin: CO
region: Colombia
---

# Accuracy: ±0.2 m/s Range: 0-15 m/s Output: 4-20 mA Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1

**Brand:** siemens
**Price:** $2254047
**Availability:** ✅ In Stock

## Summary

> 🚀 Elevate Your Airflow Game!

## Quick Answers

- **What is this?** Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1 by siemens
- **How much does it cost?** $2254047 with free shipping
- **Is it available?** Yes, in stock and ready to ship
- **Where can I buy it?** [www.desertcart.co](https://www.desertcart.co/products/185057418-air-velocity-sensor-range-0-to-5-10-15-m)

## Best For

- siemens enthusiasts

## Why This Product

- Trusted siemens brand quality
- Free international shipping included
- Worldwide delivery with tracking
- 15-day hassle-free returns

## Key Features

- • **Robust Performance:** Designed for extreme conditions, operating in temperatures from -10°C to 45°C with 95% RH.
- • **Flexible Installation:** Customize your setup with a mounting flange that allows for variable probe insertion lengths.
- • **Precision Flow Control:** Experience unparalleled accuracy with a graduated probe ensuring maximum flow precision.
- • **Vibration Minimization:** Say goodbye to interference with our dampening gasket that minimizes vibrations.
- • **User-Friendly Output Options:** Choose between 4-20 mA or 0-10V DC outputs to suit your system needs.

## Overview

The Siemens QVM 62.1 Air Velocity Sensor is engineered for precision in pharmaceutical clean rooms and HVAC applications. With a selectable range of 0 to 15 m/s, it offers exceptional accuracy and flexible installation options, making it the ideal choice for professionals seeking reliable airflow measurement in demanding environments.

## Description

Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1

## Features

- Features: The mounting flange allows the installer to vary the probe insertion length into the duct space for best control | Mounting flange dampening gasket minimises vibration | Graduated probe ensures maximum flow accuracy | Flow directional arrow provides for the most accurate reading | Connection cable provides mounting flexibility
- Range: 0 to 5 m/s | Accuracy: ±0.2 m/s + 3 % of measured value at Temp: 20 °C, 45% RH, 1013 hPa: ±0.65 m/s | Resolution: 0.1 m/sec | Frequency: 50/60 Hz | Output: Voltage: 4 to 20 mA or 0 to 10V DC (User Selectable) | Current: ±1 mA. | Immersion Length: 327 mm
- Operating Temperature: -10°C to 45°C | Humidity (non-condensing): 95% RH | Storage Temperature: -30°C to 60°C, Humidity (non-condensing): 95% RH
- Operating Voltage: 24V AC ±20% | Connection, electrical: Screw Terminals | Cable length: 1 meter | Degree of Protection: IP 42 | Dimensions: 86 x 43 x 117 mm
- Supply Scope: 1 Unit of QVM62.1 Air Velocity Sensor, Duct Mounting Flange and Instruction Manual | Applications: Ducts, Outlets, Laboratories, Pharmaceuticals Cleanrooms Environments, Refrigerators,Laminar and AHU's.

## Technical Specifications

| Specification | Value |
|---------------|-------|
| Brand | Siemens |
| Manufacturer | Siemens |
| Country of Origin | Germany |
| Number of Memory Sticks | 1 |
| Item Weight | 500 g |
| Package Dimensions | 5 x 5 x 5 cm; 500 g |
| Item part number | Hold Siemens QVM 62.1 |

## Images

![Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1 - Image 1](https://m.media-amazon.com/images/I/21bHuYgBiyS.jpg)
![Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1 - Image 2](https://m.media-amazon.com/images/I/214VQrTkGvL.jpg)
![Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1 - Image 3](https://m.media-amazon.com/images/I/21uv5840bdL.jpg)
![Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1 - Image 4](https://m.media-amazon.com/images/I/31rAKDSAj0L.jpg)
![Air Velocity Sensor(Range: 0 to 5/10/15 m/s Selectable with 4-20mA Transmission) for Pharmaceutical Clean Rooms, HVAC Model: Siemens QVM 62.1 - Image 5](https://m.media-amazon.com/images/I/31LNokfgwnL.jpg)

---

## Why Shop on Desertcart?

- 🛒 **Trusted by 1.3+ Million Shoppers** — Serving international shoppers since 2016
- 🌍 **Shop Globally** — Access 737+ million products across 21 categories
- 💰 **No Hidden Fees** — All customs, duties, and taxes included in the price
- 🔄 **15-Day Free Returns** — Hassle-free returns (30 days for PRO members)
- 🔒 **Secure Payments** — Trusted payment options with buyer protection
- ⭐ **TrustPilot Rated 4.5/5** — Based on 8,000+ happy customer reviews

**Shop now:** [https://www.desertcart.co/products/185057418-air-velocity-sensor-range-0-to-5-10-15-m](https://www.desertcart.co/products/185057418-air-velocity-sensor-range-0-to-5-10-15-m)

---

*Product available on Desertcart Colombia*
*Store origin: CO*
*Last updated: 2026-01-30*